Need a book? Engineering books recommendations...
RE:basement uplift follies[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: seaint(--nospam--at)seaint.org
- Subject: RE:basement uplift follies
- From: Michael Davis <michael.davis(--nospam--at)ferc.fed.us>
- Date: Thu, 30 Jul 1998 09:16:14 -0400
"Jeff Smith" <smthengr(--nospam--at)sirius.com> wrote: >A while back I posted some questions on a ski chalet basement. The >retaining walls are over 21 feet tall on the high sides and the potential >water table creates at least 14' of head. The project will only get to the >ground floor before they cover it up for the winter. I have a net >hydrostatic uplift of about 300 psf. so I need to fill up the basement with >some counter balance. I do not want to add piers because it will >penetrate the membrane. So I am left with filing up the basement with >about 5 feet of water. I am concerned that when the water freezes it >will damage the walls. There probably will not be power to heat the >water or to provide pumps. Alternatives include borrowing some chair >lift counter balance blocks, caltrans lane dividers, or install water tanks. Anyone have any ideas? >I explained to the geotech that the basement was for a squash court. >The geotech told me that he has played squash and that the game is not >*that* great. Do you have any plans for a drainage system underneath the slab or behind the walls? A properly designed and installed drainage system can effectively eliminate the uplift forces. Another option is to drill shallow wells (30 to 40 feet) and install pumps in the ground outside of the building. I have seen this done for hydropower plants in Nebraska that effectively reduce the phreatic level below the foundation of the plant. Of course, you will need to get power to the site to do this and have someone regularly check the pumps and the phreatic level in the wells. Either way, this would eliminate the need to counter act the uplift force. The slab could heave if the water below the slab is not drained away and it freezes, no matter how heavy the counterweight is. I hope this helps. Good luck. Michael S. Davis, P.E.
- Prev by Subject: Re: basement uplift follies
- Next by Subject: Re: RE:basement uplift follies
- Previous by thread: Re: basement uplift follies
- Next by thread: Re: RE:basement uplift follies