Need a book? Engineering books recommendations...
FW: Hip Roof Diaphragm answer from SEAOC[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: "'SEAOC'" <seaoc(--nospam--at)seaoc.org>
- Subject: FW: Hip Roof Diaphragm answer from SEAOC
- From: "wtca" <wtca(--nospam--at)classic.msn.com>
- Date: Tue, 25 Aug 1998 18:12:11 -0500
Mr. Sherman: AF&PA and APA are a good source for basic wood diaphragm design. AF&PA?s help desk telephone number is 202/463-4713 and APA?s telephone number is 253/565-6600. These two groups provide the best industry information on diaphragm design and this design is independant of the structural wood member being used to support the diaphram. Special considerations when trusses are the structural support system include: Any trusses that are to be used as drag struts should be clearly indicated on the structural framing plan. Please be sure to provide the magnitude of the forces, the means by which they are to be applied to the truss and transferred from the truss to the shearwalls. Also, if the roof sheathing at the hip ends breaks above the joint between the end jacks and the supporting girder truss, the lateral forces to be resisted by the end jacks should be specified so that an appropriate connection can be provided to resist these forces. I hope this helps. Please let me know if we can be of any further assistance in this matter. Jim Vogt, P.E. Technical Services -----Original Message----- From: Bill Sherman [mailto:SHERMANWC(--nospam--at)cdm.com] <mailto:[mailto:SHERMANWC(--nospam--at)cdm.com]> Sent: Wednesday, August 19, 1998 7:47 AM To: seaint(--nospam--at)seaint.org Subject: Wood hip roof diaphragm A co-worker of mine is designing a building with a hip roof, using wood trusses and a plywood diaphragm, and with vents at the ridge line. We don't do a lot of wood design here and would like some information on limitations on such a design. How do you determine the diaphragm capacity of such a hip roof? Are there limits on roof slope vs diaphragm capacity? How do you handle ridge vents relative to diaphragm shear connections? Thanks in advance for any assistance.
- Prev by Subject: RE: higher loads or better details.
- Next by Subject: hoping you'll change your mind
- Previous by thread: RE: 1950's steel joist catalog
- Next by thread: Application for Structural drafter