Need a book? Engineering books recommendations...
RE: Vapor Barriers[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: seaint(--nospam--at)seaint.org
- Subject: RE: Vapor Barriers
- From: Michael Davis <michael.davis(--nospam--at)ferc.fed.us>
- Date: Thu, 15 Oct 1998 09:37:56 -0400
"Caldwell, Stan" <scaldwell(--nospam--at)halff.com> wrote: >"the vapor barrier is just intended just stop upward vapor transmission. >That is why I think it may be OK to punch holes in the vapor barrier" >Huh! I don't get it, y'all! Why bother to put down a visqueen barrier >if you intend to poke holes in it? If you had a boat, would you >purposely poke holes in the hull? Since the purpose of the visqueen is >to keep moisture out of the floor, whether liquid or vapor, any >penetrations are detrimental. Besides, the contractor will usually find >creative ways (rebar, crushed stone) to puncture the visqueen without >any help from the engineer! Stan, The main purpose of using a vapor barrier is to reduce the humidity level in the building to reduce or eliminate condensation problems. The holes in the boat analogy is not a good one - rather, the barrier is more like housewrap, it doesn't stop the wind from washing the heat out of the walls in the winter, but it does slow it down considerably. If you have a few small areas where the housewrap is not sealed properly, it's not going to make much of a difference to your fuel bill. Likewise, a few small holes in the vapor barrier is not going to significantly increase vapor transmission. Vapor transmission requires a large surface area to move a lot of moisture. A small amount of vapor transmission can be handled by the natural (or mechanical) ventilation of the building. Have you ever been in a crawlspace of an older home where there is no vapor barrier, but just an exposed soil surface? I've read that several gallons of water evaporate from the soil daily into these homes, resulting in condensation on the joists and subsequent rot. Installing the barrier with a layer of gravel to hold it down and protect it makes a huge difference, substantially lowering the humidity level in the crawlspace and in the house. Vapor barriers aren't designed to stop water penetration. If this is a concern (and it usually is!), then drain pipes along the footing leading to a sump pump or lower ground outside should be installed. Michael S. Davis, P.E.
- Prev by Subject: RE: Vapor Barriers
- Next by Subject: Re: Vapor Barriers
- Previous by thread: RE: Vapor Barriers
- Next by thread: Vapor Barriers