Need a book? Engineering books recommendations...
Re: UBC 1997 - Non building structure - Section 1632.2 for A.bolt design[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: <seaint(--nospam--at)seaint.org>
- Subject: Re: UBC 1997 - Non building structure - Section 1632.2 for A.bolt design
- From: THunt(--nospam--at)absconsulting.com
- Date: Tue, 24 Dec 2002 08:31:27 -0800
It depends on the stiffness of your "pedestal". If this is a grade mounted equipment sitting on top of a solid concrete mat (with period T less than 0.06 second) then you should probably be looking at UBC Section 1634.3, "Rigid Structures" and equation 34-1. As your equipment gets elevated and the support gets more flexible (and more building like), such as a concrete moment frame, then you need to take into consideration the amplifications of the support structure and the application of Section 1632.2 and equation 32-2.
Thomas Hunt, S.E.
|"Vasu, Ravi" <Ravi.Vasu(--nospam--at)jacobs.com>
12/24/2002 07:53 AM
Subject: UBC 1997 - Non building structure - Section 1632.2 for A.bolt design
Please refer to Lateral force per section 1632 & 1632.2 (UBC 1997).
For equipments supported on concrete pedestals (T.O.C. at grade)
The critical force for the design of Anchor bolt will be per
section 1630.2 / eqn. 32-2 / eqn. 34-1 (depends on flexible or rigid)
In this, for pedestals at grade, hx = 0 in the equation 32-2.
My question is,
What is the minimum height for pedestal T.O.C.(top of concrete) above grade,
so that hx can be taken (or about) 0. For example, if the pedestal TOC is about 2 or 3 or 4' above grade,
(for small heights above grade)
Fp increases almost 4 times than it is at grade(per eqn. 32-2).
The critical force for the A.bolt can be very high.(than it is at grade).
I could not find any reference or example in 'Seismic design manual' . Any guidance in this is
Ravi Vasu, P.E.,
NOTICE - This communication may contain confidential and privileged information that is for the sole use of the intended recipient. Any viewing, copying or distribution of, or reliance on this message by unintended recipients is strictly prohibited. If you have received this message in error, please notify us immediately by replying to the message and deleting it from your computer.
- Prev by Subject: UBC 1997 - Non building structure - Section 1632.2 for A.bolt design
- Next by Subject: UBC 1997 - Rebar development length & Splice length
- Previous by thread: UBC 1997 - Non building structure - Section 1632.2 for A.bolt design
- Next by thread: Re: UBC 1997 - Non building structure - Section 1632.2 for A.bolt design