I had this conversation with some PEMB manufacturers a while back. The
authors of Design Guide 3 intended this for use for the PEMB industry. They
do a lot of work for that industry. Some manufacturers will balk, but the
recommendations of Design Guide 3 are reasonable. There are no building
code wind drift limits since this is a serviceability issue and is not a
We create a one page performance spec for PEMB. The MBMA had some
commentary stated that you should calculate lateral drift and some owners
don't like it when the lights sway. The practice for better PEMB
manufacturers is to limit lateral drift to h/30 for a 10 year wind, and
h/100 if you have masonry. That is not restrictive enough. Again what is
reasonable is contained in Design Guide 3.
You will have to put it in your specification. Don't just reference DG 3.
It is not a manditory code. You can make it manditory by specifying the
recommendations in DG 3 as "required", but that creates a layer of
ambiguity. I specify the maximum lateral drift and under a given loading
that is to occur. DG 3 uses a 10 year wind for servicability. I also
specify the maximum girt and purlin deflections.
From: "Bruce Holcomb" <bholcomb(--nospam--at)brpae.com>
Subject: RE: PEMB's and lateral deflection
Date: Thu, 7 Apr 2005 09:07:04 -0500
In addition to Code prescribed deflection limits, we use AISC Design
Guide 3 - Serviceability and AISC Engineering Journal, First Quarter,
1993 for serviceability limits, but neither of these is directly for
metal building systems. The Metal Building Manufacturers Association
(MBMA) has their own manual which (if I remember correctly) has
recommended deflection and sidesway limits. I no longer have a copy, so
I can't quote it. But you can order one from MBMA.
Any current metal building systems designer out there who can elaborate?
Bruce D. Holcomb, PE, SE
Structural Engineer & Vice President
Butler, Rosenbury & Partners
From: Jim Wilson [mailto:wilsonengineers(--nospam--at)yahoo.com]
Sent: Thursday, April 07, 2005 8:53 AM
Subject: PEMB's and lateral deflection
Are there any official industry position statements or
articles on coordinating maximum lateral deflection of
PEMB's with rigid masonry facades? I am looking for a
little more "oomph" to add into a letter to a future
James Wilson, P.E.
* Questions to seaint-ad(--nospam--at)seaint.org. Remember, any email you
* send to the list is public domain and may be re-posted
* without your permission. Make sure you visit our web
* site at: http://www.seaint.org******* ****** ****** ****** ******* ****** ****** ********