Need a book? Engineering books recommendations...
RE: Freezer slabs[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: <seaint(--nospam--at)seaint.org>
- Subject: RE: Freezer slabs
- From: "Stuart, Matthew" <mstuart(--nospam--at)schoordepalma.com>
- Date: Mon, 25 Jul 2005 12:00:38 -0400
You will need to provide a 3-inch mudslab (which serves to both contain the underslab heating and provide a substrate for the underfloor insulation), a layer of underfloor insulation (6-inch minimum I would guess for 0 to 10 degrees) and an unreinforced wearslab for support of the pallets and racks.
I have some standard details I can send you if you would like.
D. Matthew Stuart, P.E., S.E.
Senior Project Manager
200 State Highway Nine
Manalapan, NJ 07726-0900
Phone: (732) 577-9000 (Ext. 1283)
FAX: (732) 431-9428
Cell: (908) 309-8657
Can anyone provide or point me in the right direction to find some standard practice and or details with regard to the various options for freezer slabs on grade?
Continuous service exposure of 0-10 degrees F.
Any help would be appreciated.
- Prev by Subject: Freezer slabs
- Next by Subject: RE: Freezer slabs
- Previous by thread: Freezer slabs
- Next by thread: RE: Freezer slabs