Need a book? Engineering books recommendations...
RE: 3rd floor in UBC97[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: <seaint(--nospam--at)seaint.org>
- Subject: RE: 3rd floor in UBC97
- From: "Truitt Vance" <Truitt(--nospam--at)AshleyVance.com>
- Date: Tue, 25 Sep 2007 11:29:02 -0700
I was hoping that you would respond!
I think I have something worked out with the city such that I can submit as con docs before 12/31 long as I get the thumbs up from the architectural board, not necessarily planning or the city council – but now I am thinking I will research this more and maybe purposefully submit after 12/31 if what you write is the case and there are no caveats! I find it really interesting that it sounds more lax than the UBC97 code so it makes me a little leery getting all these approvals and then submitting under an entirely new code, I think I have the new code coming but unfortunately it is not here yet.
Aren’t architects just going nuts with these changes? Most projects around here take 2 years to get approved, nothing like going through a major code cycle mid stream of the planning process.
I have heard area separation walls/fire walls are changing also, I use the NFPD 13-D for this configuration, then (2) 1 hour walls between the condo units. Do you know if the new code going to be similar? I have heard that fire walls are going to be changed dramatically but I don’t know how yet.
Thanks for the input.
From: Ben Yousefi
IBC does not seem to address this based on the story designation. It is addresses it based on the space and building as a whole. 1015 limits the number of exits from any space (floor) by the occupant load and travel distance. If you have less than 10 occupants (2000 sq. ft.) and travel no more than 75 feet to get to the outside you are OK with one exit. 1019 limits the number of buildings with one exit and it gives a blanket approval for one exit in any R3 (dwelling) building. So, unless you have very large floor area (more than 2000 square feet) and the travel distance from 3rd floor to the outside is greater than 75 feet you should be OK with one exit. Of course, I am a new 2006 IBC user and may be missing something.
Ben Yousefi, S.E., C.B.O
(310) 458-2201 x 5025
From: Truitt Vance
I know this is an architectural question but you guys are smart so I am sure I will get an answer...
The UBC97 allows 3rd floors (residential occupancy, carriage or townhome style, attached multifamily units) up to 500 square feet, and then requires a second egress to grade separated by more than half the distance of the hypotenuse of the building. However, if you can make the second level qualify as the “story, first” (as defined in section 220) you can “work around” this requirement by designing the site to have retaining on at least half the perimeter of the building over four feet.
My big concern is if there is a similar rule/exception in the
IBC06 that will allow me to get third stories over 500 square feet using a
similar configuration. Does anyone know if this 500 sq ft
limitation even exists in third stories under the IBC? If it does, is
there a way to design the buildings with a larger third story and not have a
second means of egress?
- RE: 3rd floor in UBC97
- From: Ben Yousefi
- RE: 3rd floor in UBC97
- Prev by Subject: RE: 3rd floor in UBC97
- Next by Subject: Re: Job Opportunity - OT - AKA "The Good Old Days" (sarcasm)
- Previous by thread: RE: 3rd floor in UBC97
- Next by thread: RE: 3rd floor in UBC97