Need a book? Engineering books recommendations...
Re: Underground gas-pipe protection[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: seaint-seaosc(--nospam--at)mail-list.com
- Subject: Re: Underground gas-pipe protection
- From: "h.d.richardson" <h.d.richardson(--nospam--at)telus.net>
- Date: Wed, 10 Oct 2012 09:08:42 -0600
- List-subscribe: <mailto:SEAINT-SEAOSCemail@example.com>
David,Sorry I did not get a chance to get back to you yesterday but I was otherwise occupied.
I have some thoughts that may or may not be useful for the solution of your problem.
1. If the location of the future crane support points is known you could build "tables" (supported on piles or otherwise) to support the crane legs.
2. If the future crane support points can not be determined in advance you might consider backfilling the excavation with "flowable fill" or a slightly stronger concrete mix. It could even be reinforced with fibres or other reinforcing if desired.
3. As a Cadillac version of #2 you could even sleeve the pipe for the entire 800 meters. You may need to provide some sleeved portion at the ends to provide flexibility for the transition from underground to concrete encased in any event.
I hope these thoughts are helpful. I'm confident that you will come up with a good practical solution.
Regards, H. Daryl Richardson----- Original Message ----- From: "David Cohen (Baran Raviv)" <dcohen(--nospam--at)barviv.co.il>
To: <seaint-seaosc(--nospam--at)mail-list.com> Sent: Tuesday, October 09, 2012 11:05 AM Subject: [SEAINT-SEAOSC] Underground gas-pipe protection
Fellow engineers,I'm designing an underground pipe for Natural Gas (12" - 6" diameter) 800m length.My client asks me to design a solution to protect the pipe for the case of loading a crane-leg above the pipe.He thinks that it could be a 500 t-m crane there. The maximum the crane could apply in one leg is 160 ton and they use a 3.8X2.4m dispersal plate (17.6 t/m²). The pipe depth is varying between 1.5 to 2.7 m.The geotech engineer doesn't collaborate so much; it's a sandy-clay soil (Ihope I'll get some more information about the soil bearing capacity and sedimentation properties.)
Truncated 1169 characters in the previous message to save energy. -------------------------------------------------------------------------Post your message to the list by sending it to: SEAINT-SEAOSC(--nospam--at)mail-list.com.
The email messages sent to the list will be saved in an archive on the World Wide Web. These archives are located at: http://archive.mail-list.com/SEAINT-SEAOSC To contact the list owner, send your message to: SEAINT-SEAOSC-list-owner(--nospam--at)mail-list.com. 5700 Ralston Street, Suite 300, Ventura, CA 93003 To unsubscribe, switch to/from digest, get on/off vacation, or change your email address, click here. http://cgi.mail-list.com/u?ln=seaint-seaosc&nm=seaintma%40euken.net
- Prev by Subject: RE: Underground gas-pipe protection
- Next by Subject: RE: Underground gas-pipe protection
- Previous by thread: RE: Underground gas-pipe protection
- Next by thread: RE: Underground gas-pipe protection