Need a book? Engineering books recommendations...
Re: Buoyancy factor of safety[Subject Prev][Subject Next][Thread Prev][Thread Next]
- To: seaint-seaosc(--nospam--at)mail-list.com
- Subject: Re: Buoyancy factor of safety
- From: Tarek Mokhtar <Tarekmokhtar(--nospam--at)earthlink.net>
- Date: Mon, 26 Nov 2012 16:28:28 -0800
- List-subscribe: <mailto:SEAINT-SEAOSCemail@example.com>
Thank you for all your responses, I guess I was trying to justify a lower F.S than the 1.67, considering that the ground water will rise to the top of grade, as Daryl suggests, and the water weights are pretty well defined, I just do not see reducing the weight of concrete by 60%
Tarek Mokhtar, SE
Doesn't the load combination 0.6D + H give you a "safety factor" of 1.0/0.6 = 1.67?On 11/26/2012 2:03 PM, h.d.richardson wrote:Tarek,Whenever I've done these I've assumed the groundwater table for buoyancy calculations was at the surface due to rain saturating the backfill. I've also considered only the soil directly above the submerged tank (or footing extension for concrete cisterns); I've not considered the soil sloping away from the tank wall at 60 degrees or anything like that. I also consider the buoyancy acting on the concrete weights or the footing.For safety factors (I prefer to call them ignorance factors) Canadian limit states codes would use 1.25 for the dead load (or other accurately determined load) being the force to be resisted and 0.85 for dead weights resisting the force. This results in 1.25/0.85 = 1.47, which is close to 1.5. I would not consider anything less than 1.5.
Truncated 321 characters in the previous message to save energy. -- -------------------------------------------------------------------------Post your message to the list by sending it to: SEAINT-SEAOSC(--nospam--at)mail-list.com.
The email messages sent to the list will be saved in an archive on the World Wide Web. These archives are located at: http://archive.mail-list.com/SEAINT-SEAOSC To contact the list owner, send your message to: SEAINT-SEAOSC-list-owner(--nospam--at)mail-list.com. 5700 Ralston Street, Suite 300, Ventura, CA 93003 To unsubscribe, switch to/from digest, get on/off vacation, or change your email address, click here. http://cgi.mail-list.com/u?ln=seaint-seaosc&nm=seaintma%40euken.net
- Prev by Subject: Re: Buoyancy factor of safety
- Next by Subject: California SE Exam Cheating Ends
- Previous by thread: Re: Buoyancy factor of safety
- Next by thread: HDPE gas pipe